4211-82-G 08-01-14 7014132 314 SKSM 104 K
INSTALLATION AND OPERATING INSTRUCTIONS Page 4
DIAGRAM 3 DIAGRAM 4
ONE HOUR OPERATING ZONE FOR 9 HOUR DELAY TIMER
This area from "OFF" to "ON" is the operating zone. This is
the only time the heater is on.
This area from "9" to "ON" is the delay zone, meaning the
heater can be programmed to come on up to nine hours
later. The heater will not operate in this area.
Sensor protective cover. Locate bottom
of sensor 5" from ceiling directly above
center of heater. (See diagram 5.)
Room light outlet box 70
inches up from oor. Do not
locate directly over heater.
(2) #14 wires and Ground AWG
90°C wire to control.
Screw control box to 2x4 blocking
Note: if sensor wire is exposed on
surface of the sauna wall cover with
Temperature control box. Face out from sauna
room ve feet up from oor.
Control circuit wire.
2x4 blocking for bracket
Flex conduit. Provide three feet
into room during rough-in.
Optional separate light circuit if control
light is used.
DIAGRAM 5, continued
sensor 5" from
Insert screwdriver tip here to unsnap
sensor cover from sensor.