220.127.116.11. Applying Commands to Several Plugs - Text Interface
As described below, switching and reboot commands can be applied to only one
Switched AC Outlet, or to an assortment of outlets.
Note: When switching and reboot operations are initiated, Boot/Sequence
Delay times will be applied as described in Section 5.7.
1. Switch Several Plugs: To apply a command to several plugs, enter the numbers
or names for the plugs, separated by a "plus sign" (+) or a comma (,). For example
to switch plugs 1, 3, and 4 Off, enter either of the following commands:
/OFF 1+3+4 [Enter]
/OFF 1,3,4 [Enter]
Note: When the "+" or "," are used, do not enter spaces between the plug
name or number and the plus sign or comma.
2. Switch a Series of Plugs: To apply a command to a series of plugs, enter the
number for the plugs that mark the beginning and end of the series, separated by a
colon. For example to switch On plugs 1 through 3, enter the following:
/ON 1:3 [Enter]
4. All Plugs: To apply a command to all plugs, enter an asterisk in place of the name
or number. For example, to Boot all plugs, enter the following:
/BO * [Enter]
Note: When this command is invoked by an account that permits only User
level command access, it will be applied only to the plugs that are allowed for