8 Stove Installation (for qualified installers only)
© Travis Industries 93508061 4150520
Floor Protection Requirements
Stove must be placed on the Travis Industries legs or Pedestal.
Floor protection must extend 6" to the sides and rear of the stove and 16" to the front of the stove
(41-3/8" wide by 42-1/2" deep - see Figure 2 and Figure 3).
Floor protection must be non-combustible and at least .018" thick (26 guage).
Stove Placement Requirements
Clearances may be reduced by methods specified in NFPA 211, listed wall shields, pipe shields, or
other means approved by local building or fire officials.
Stove must be placed so that no combustibles are within, or can swing within (e.g. drapes, doors), 36"
of the front of the stove
If the stove is placed in a location where the ceiling height is less than 7', it must follow the
requirements in the section "Alcove Installation Requirements"
Must maintain the clearances to combustibles listed below (drywall, furniture, etc.):
The following clearances must be met (see Figure 2 and Figure 3)
Minimum Clearance Singlewall
A Sidewall to stove 16" 16"
B Backwall to stove 15” 10"
C Cornerwall to stove 9-1/2" 7-1/2"
D Connector to sidewall 27-3/4" 27-1/4"
E Connector to backwall 17-3/4" 12-1/4"
F Connector to cornerwall 21" 18-1/2"
* Reduced clearance installations require one of the chimneys and connectors listed below:
AMERI-TEC model DCC with model HS chimney
DURAVENT model DVL with DURATEC or DURA-PLUS chimney
METALFAB model DW connector with TG chimney
SECURITY model DP connector with SECURITY model ASHT or S2100 chimney
Standard Masonry Chimney with any one of the above listed connectors
NOTE: Reduced clearance connectors may not connect to the flue collar – an appliance adapter may be required.
NOTE: Standard residential installations with reduced clearance connector may use the clearance
determined by the manufacturer of the connector for the connector to wall clearance or the clearance
listed in this manual. Offsets must be used to maintain the stove to wall clearance.